New Assemble Split Ac Service In Delhi NCR
Split AC Assemble starts with deciding the situation of indoor and outdoor unit of air conditioning. After the situation is confirmed, installation of indoor unit is started.
A Split AC unit has following parts:
Indoor unit Outdoor unit also called external unit
Wall bracket ( Optional)
Split AC Assemble requires following tools:
Basic tool box
What is included in Split AC installation/ Assemble?
Making the marks as per wall bracket: within the split AC box, there's an aluminum wall bracket with all the required holes and attachments. The indoor unit of split AC is fixed on this bracket. to start out the split AC indoor unit installation, holes are marked on the wall as per the bracket.
Drilling holes within the wall: After the holes are marked on wall, the wall bracket is removed and holes are made within the wall with a drilling machine at the marks. Thereafter the bracket is fixed with the screws within the drilled holes.
Passing important pipes and cables through wall: After the bracket is fixed on the wall, a hole (of large diameter) is drilled across the wall to pass copper pipes called refrigerant tubing, drain hose and cable to attach the indoor unit with the outdoor unit of split AC.
Installing the indoor unit of split AC: Now split AC indoor unit is securely mounted on the wall bracket. Thereafter the copper pipes (coupled to the indoor unit) are skilled the opening drilled across the wall. The drain pipe connected to at least one end of the indoor unit is skilled an equivalent hole and is left free within the open space for water drainage.
Installing the outdoor unit of split AC: The outdoor unit of split AC is sort of heavy, so it should be handled carefully. The outdoor unit of split AC is brought outside to the situation where it's to be installed. The outdoor unit also can be mounted on an external wall with the assistance of support. The wall on which the outdoor unit is being fitted should be strong enough in touch its weight and vibrations. Installation of copper pipes and electrical connections: Once the indoor and therefore the outdoor units of the split air conditioning are fitted, the copper pipes connecting the 2 units are installed. The copper pipe attached to the indoor unit is connected to the outdoor unit. Finally the electrical cable is skilled the opening to attach the indoor unit of split AC to outdoor unit of split AC.
Final check: After the indoor unit of split AC, outdoor unit of split AC, copper pipes, drain hose and every one electrical connections of split AC are accurately installed, the air conditioning is switched on to see if it's works properly.
Important guidelines for split AC installation/ Assemble
The indoor unit of split AC must be installed on a wall strong enough to carry the unit’s weight.
The indoor unit of split AC requires a minimum of 15 cm of open space surrounding its top and sides for correct air flow.
The indoor unit of split AC should be mounted at a height of 7-8 feet above the bottom for adequate cooling inside the space
While fixing the aluminum bracket on wall confirm that the bracket is given a small angle, in order that the indoor unit of split AC, when fitted is additionally at a small angle to enable unrestricted flow of the condensed water from the drain pipe.
For proper cooling the indoor and outdoor units of split AC should be mounted at location faraway from direct sunlight.
The outdoor unit of split AC must be placed on a flat and rigid surface. This unit contains key components of split AC like compressor, condenser, fan motor etc. If the unit isn't placed on a flat surface then it'll vibrate excessively, which may cause the breakage of copper pipes, coolant leakage and compressor/condenser damage. Further, the vibrating unit makes many noise which could disturb you and your neighbors.
Correct distance between the indoor and outdoor unit plays a really important role in cooling. The coolant at very coldness flows inside the copper tubes between indoor and outdoor units of split AC. there's always some loss of cooling effect to the atmosphere when the refrigerant flows between the units. Hence to scale back this loss, the space between the indoor unit of split AC and therefore the outdoor unit of split AC should be kept as minimum as possible. the utmost allowable distance between the indoor and therefore the outdoor units of split AC are often about 15 meters.
The outdoor unit of split AC should be installed in open space in order that there's no hindrance to the warmth dissipated from the condenser.